♦ Aluminum housing, DIN format 96 x 96 mm.
♦ Operating delay time can be selected by software starting from 200 ms. Up to 2400 ms.
♦ Built-in three push buttons for Acknowledge, Reset and Test
♦ The label is a single paper sheet which slides into a small transparent envelope recessed in the front panel.
♦ All inputs are isolated with opto-couple, NO or NC volt-free contact can be selected by software.
♦ Alarm sequences (Auto/Manual Reset /Indicator) of each input can be selected by software.
♦ Alarm sound type (Bell/Buzzer) of each input can be selected by software.
♦ Integrated two test functions (Lamp Test & Function Test) in one push button (“TEST”)
♦ Time of auto acknowledge function can be set from 1-240 seconds.
♦ Built-in heart beat function which illuminated by LED lamp to display healthy status as self-supervision function.
♦ Supervisory contact (watchdog) for warning status
♦ Communication port : USB for configuration, RS485 – Modbus RTU for serial interface
♦ Alarm monitor software for remote monitoring and control ( Ack / Reset / Test )
♦ Relay output module : The auxiliary contact output or repeat relay module, normally used for
remote alarm or remote control as given design
When an alarm signal is occurred, it will initiate Bell/Buzzer to operate. Meanwhile, it will produce output direct to the display LED, which makes LED flicking. After pressing an acknowledged push button, Bell or Buzzer remains silence but LED is steady on. If an alarm signal is return to normal status then the alarm is cancelled. However, the light of the indicating display LED will be sustained. Unless the reset push button switch is activated. Then the LED will be turn off and return to its initial condition. The “TEST” push button includes two functions; the first function is “Lamp TEST” if push and hold this push button less than 3 seconds, it will light up all LED lamps at the front panel only. The second function is “Function Test” if push and hold this push button more than 3 seconds, the LED lamp will start flicking and Bell/Buzzer alarms. This “TEST” push button is provided for checking purpose of all LED and operating functions at normal condition. While checking all LED and suddenly some of the alarm signals are occurred, the alarm sequence will be operated as usual without effect from the lamp test sequence. Alarm sequence can be selected by software for manual reset sequence or auto reset sequence as described as below.
SEQUENCE1 : MANUAL RESET
When an alarm signal is occurred, the LED would gently flash and Bell or Buzzer will activate continuously. To stop the sound of Bell or Buzzer, “ACK” push button has to be pressed. Then Bell/Buzzer is silenced but LED is still steady on. Reset is only possible by pressing “RESET” push button when alarm input returns to normal status.
SEQUENCE2 : AUTO RESET
When an alarm signal is occurred, the LED would gently flash and Bell or Buzzer will activate continuously. To stop the sound of Bell or Buzzer, “ACK” push button has to be pressed. Then Bell/Buzzer is silenced but lamp is steady on. Auto reset will take place simultaneously when alarm input returns to normal status.
INPUT INDICATOR FUNCTION
This function is same as indicator lamp. When an alarm signal feed through an assigned input of Annunciator, the LED display lamp of that design fault will lid or steady on. After alarm input returns to normal then the display lamp will automatically switch off.
Connection diagram at the rear side of ESPAN04